Purogene Long Term Water Storage Treatment Method is an EPA approved Water Storage Treatment Method, Purogene is one of the best
water purification methods for drinking
water available today
and has been The most widely used water purification treatment. Purogene can
also be used to Disinfect Potable Water Storage Tanks, and treat water for long term storage
PUROGENE is a 2% solution of stabilized chlorine dioxide, ClO2 (contains no free chlorine).
dioxide is recognized safe for drinking water treatment for more than 50 years. It is EPA registered for use in drinking water.
some water treatments that take hours to work and leave a bad after-taste, 3R PUROGENE makes water fresh the moment it enters the container, from a drinking glass to a plastic, metal, or fiberglass storage tank.
PUROGENE is non-toxic and biodegradable, presenting no harm to the environment or the user.
ounce of 3R PUROGENE will purify thirty (30) gallons of drinking water, as well as control the build-up of slime and odor-causing bacteria in any drinking water system in RV units, campers, trailers, and boats.
treatment to control build-up of slime and odor-causing bacteria and enhance the taste of stored drinking water.
water should be treated at a rate of 1 fl oz (2 tablespoons) of 3R PUROGENE per 30 gallons of water (5 ppm ClO2 concentration). This treatment will provide bacteria growth control, fresh taste and odor control to the water.
each new addition of drinking water to the fresh water tank at the ratio of 1 fl oz (2 tablespoons) of 3R PUROGENE per 30 gallons of drinking water.
as often as necessary to maintain fresh taste and odor control.
the drinking water system (50 ppm ClO2 concentration): Place 1/3 fl oz (2 teaspoons) of 3R PUROGENE per gallon of water tank capacity (example: 30 gallon tank x 1/3 = 10 fl oz of 3R PUROGENE) into a clean plastic or glass container. To this add 1/2 tsp of Citric Acid Activator Crystals (lemon juice may be used, same amount) per ounce of Purogene (4 ounces citric acid/quart Purogene) and let it stand for 5 minutes.
NOT breathe the fumes! Pour the sanitizing solution into the water tank and fill the tank with potable water. Turn on the water pump and drain a small amount of water from each of the faucets including hot water faucets so that the sanitizing solution gets into the entire system. Then refill the tank with potable water to replace drawn off solution. Let the system full of sanitizing solution stand for at least 1 hour. After the hour, drain the tank and refill with potable water treated with 5 ppm of ClO2 as described above. Draw off some water from all faucets including the water heater tank to purge the sanitizing solution.
maintain the tank, repeat this procedure as often as necessary.
Note: Citric acid crystals are added at the rate of 4 ounces per quart of Purogene. Example: 100 gallon tank = 32 ounces of Purogene + 4 ounces of Citric Acid Crystals 1 tablespoon = 3 teaspoons, 1 ounce = 2 tablespoons
LONG TERM STORAGE OF WATER WITH 3R PUROGENE
: Water Storage containers must be free of oil, detergent, ammonia, and organic contaminates.
Do not use steel water Drums or steel Drums with exposed metal which will come in contact with the stored Water. Steel Barrels must be plastic lined.
The water to be stored must be potable (safe to drink). Low mineral content is preferred (reverse osmosis or distilled). Water should be bacteria free and free of organic materials.
Put 1 ounce (2 tablespoons) of Purogene for each 30 gallons of container capacity into the container. Fill the container with potable water and seal it air tight.
Store the container out of sunlight and in as cool a place as possible.
that are not completely opaque and are stored in a location that might be exposed to even a small amount of sunlight must be covered with a completely opaque cover (such as heavy gauge black plastic).
to sunlight will deteriorate the Purogene and render it ineffective in microbial control.
CHECK AND RETREATMENT
ClO2 concentration in the stored water must be checked at least once a year.
containers stored at high temperatures or may have been exposed to sunlight (semi-opaque or non-opaque) the water should be checked more frequently.
Using a ClO2 (Chorine Dioxide, the active ingredient in Purogene) test kit or test strips, check the stored water for ClO2 concentration. If the ClO2 concentration is .5 PPM (1/2 Part Per Million) or less,
The water with Purogene at the rate of 1 ounce (2 tablespoons) per 30 gallons.
Check for clarity and odor. If water is cloudy or odor is objectionable, it is recommended to discard the water.
should then be cleaned and disinfected in accordance with the “Disinfecting the drinking water system” on the other side of this document before using again for storing water.